How to install Fontana Commercial Chrome Wall Mounted XT5 Automatic Sensor Faucet | FSXT50
Easy step by steps installation instructions for Sensor Faucet
Visit Product Page
Before you begin, please read the installation instructions below. Observe all local building and safety codes.
Unpack and inspect the products for any shipping damages. If you find damages, do not install.
Please note all products must be installed by a professional and certified plumber otherwise warranty might be voided.
Sensor Faucet Installations Instructions
Minimum operating pressure 0.5 bar Maximum operating pressure 5 bar
Correct way for Hose
For ease of installation, the faceplate and battery can be disconnected from the unit at the connectors. Faceplate and Spout
Remove the back connector from the spout. Push the connector through the hole in the faceplate and screw into the spout. Secure in position with the two fixing screws.
Make sure that the spout hole is in the 12 o’clock position and the spout is pointing downwards.
Note: Please do not install this product opposite or near any reflective surfaces as this may lead to false or permanent activation.
Before installing your new mixer, flush through the pipework to ensure removal of debris, turn off the water supply.
The valve must be set into the wall to depth of 80 mm.
If you are fitting the valve to a partition wall or a wall of particularly soft substrate you will need specialist fixings.
Select the position for the valve and offer the shower valve to the wall, mark the fixing points with a suitable pencil, there are 2 pre-drilled holes in the back of the unit. Remove the valve from the wall, drill the holes to a suitable depth for the wall plugs and secure with suitable screws Connect the flexible hose coming from the unit onto the spout, making sure that the rubber washer is in place. Sensor connections
Connect the plug coming from the valve unit to the socket coming from the sensor. Power connections
Connect the socket coming from the transformer to the plug coming from the sensor.
Undo the screw on the top and remove the lid. Insert the 4 batteries into the base, according to the diagram in the bottom of the base. Replace the lid making sure that the 2 springs are orientated to match the negative ends of the 2 batteries (right).
Connect the plug coming from the transformer to the socket coming from the battery.
Slide the two tabs in the top of the faceplate over the faceplate lip, and secure in position with the screw on the underside.
Please ensure that enough access is left for the screw to be removed/inserted, during any routine maintenance.
Turn on the water.
Flexible Connecting Hose Care must be taken when connecting the flexible connection hose from the power supply box to the spout to ensure it does not bend sharply and kink or twist. See above for recommended ways to fit the flexible connecting hose.
Important: Failure to follow these guidelines may result in poor performance and damage to the flexible connection hose.
This Chrome-plated cast Brass Leo Electronic Bathroom Faucet Reduces the transfer of germs by preventing cross-contamination and re-contamination of germs and bacteria by not touching the faucets or handles. Fits all standard US plumbing. Uses 4AA Alkaline Batteries (purchase separately). Water Pressure: 0.5 - 7.0 KGS/cm, 10-125 psi. Sensitive sensor with Infrared AI smart-chip. Convenient to maintain with built-in strainer to prevent sundries from entering the solenoid valve and the strainer is easy to clean.
Brand Name: FontanaShowers
Model Number: FSXT50
Type: Motion Sensor Sink Faucet
Finish: Solid Brass/Chrome
Diameter of outlet pipe: DN15
Water Pressure: 0.05Mpa - 0.7Mpa
Power and Voltage: AC.220V - 50/60Hz, DC.6V
Power Consumption: 0.5MW, <2W
Ambient Temperature: 1 - 45 ℃ / 33.8 -113 °F
Usage: Commercial / Residential
Ideal for commercial use applications in public restrooms, restaurants, office building, public facilities, hospitals. Fits all standard US plumbing.