How to install Bravat Trio Commercial Automatic Touchless Bathroom Faucet Oil Rubbed Bronze Finish | FS-201RB
Easy step by steps installation instructions for Commercial Sensor Faucet Matt Black
Before you begin, please read the installation instructions below. Observe all local building and safety codes.
Unpack and inspect the touchless faucet for any shipping damages for any shipping damages. If you find damages, do not install.
Please note all showers must be installed by a professional and certified plumber otherwise warranty might be voided.
Sensor Faucet Installations Instructions
Step 8: (Correct way for Hose)
1. Before installation, please make sure the power is turned off.
2. When connecting the control line and power line according to the arrow, please note the male and female to prevent the circuit board from burning out, because of the incorrect connection.
3. Be sure the washer installed to prevent impurities into the water valve
to avoid leakage.
4. Overtime protection: Continuous induction water for more than 60 seconds, it will stop automatically.
5. When abnormal (No Induction but water out etc.), hold down the reset switch on the sensor box 3 seconds then release
(When press the reset switch the sensor does not action), the control circuit repower, return to normal.
Flexible Connecting Hose Care must be taken when connecting the flexible connection hose from the power supply box to the spout to ensure it does not bend sharply and kink or twist. See above for recommended ways to fit the flexible connecting hose.
Important: Failure to follow these guidelines may result in poor performance and damage to the flexible connection hose.
Flow pressure: min. 0.5 bar - recommended 1 – 5 bar
Operating pressure: max. 10 bar
Test pressure: 16 bar
Flow rate at 3 bar flow pressure for basin: ≥ 12 L/min
Hot water inlet temperature: max. 80°C
Recommended (energy saving): 60°C
Environment temperature: 5°C ~ 45°C
Dc type: AA Size 1.5V Battery，4 pcs Ac type (for European standard):
Input 220V, Output 6V/500mA
Sensing Distance: 16-20 cm
Sensing Duration: 1 second
Battery Lift Time: Appr. 50,000 cycle
Supply Water Pressure: 0.5-5 kgf/cm2
Ambient Temperature: 5°C - 45°C (Supply Water Temperature 5°C - 50°C)
Supply Water Pipe Specification: G1/2
Non-working Power Consumption: ≤0.5 mW
Reduces the transfer of germs by preventing cross-contamination and re-contamination of germs and bacteria by not touching the faucets or handles. Cut down on water usage by minimizing waste of water while soaping, lathering, scrubbing and drying hands by eliminating unnecessary and unattended water flow.
Diameter of inlet pipeDN15
Diameter of outlet pipeDN15
Water Pressure0.05Mpa - 0.7Mpa
Power and VoltageDC.6V / AC.220V - 50/60Hz
Detection ZoneFactory set 25cm/10" (based on standard inductive board)